Is your AS400 communicating with the Best UPS? If so, is it receiving a
power failure signal? If so, do you have a job that has the ups message
queue allocated. If yes to all but the last, that is causing your power
down. Check the system value QUPSMSGQ. IF it is QSYSOPR change it. After
the next failure, check the new message queue specified in the system value.
Christopher K. Bipes mailto:ChrisB@Cross-Check.com
Sr. Programmer/Analyst mailto:Chris_Bipes@Yahoo.com
CrossCheck, Inc. http://www.cross-check.com
6119 State Farm Drive Phone: 707 586-0551 x 1102
Rohnert Park CA 94928 Fax: 707 586-1884
If consistency is the hobgoblin of little minds, only geniuses work here.
Karen Herbelin - Readers Digest 3/2000
From: Scott Swaim [mailto:email@example.com]
Sent: Tuesday, January 02, 2001 8:44 AM
Subject: Abnormal Power Downs
I am experiencing Abnormal Power downs. It happens at random times. The
system is connected to a BEST Fortress UPS. Their are other things
connected to the UPS that have not powered down. I think the UPS is OK. My
IBM SE has replaced the Power Supply and the MFIOP. Does anybody have any
other suggestions of where to look?
| This is the Midrange System Mailing List!
| To submit a new message, send your mail to MIDRANGE-L@midrange.com.
| To subscribe to this list send email to MIDRANGE-L-SUB@midrange.com.
| To unsubscribe from this list send email to MIDRANGE-L-UNSUB@midrange.com.
| Questions should be directed to the list owner/operator: firstname.lastname@example.org
This mailing list archive is Copyright 1997-2019 by midrange.com and David Gibbs as a compilation work. Use of the archive is restricted to research of a business or technical nature. Any other uses are prohibited. Full details are available on our policy page. If you have questions about this, please contact