At your data center yes. Not in ours.
In ours the hot aisle is completely enclosed with storm doors on both
ends and plates from the top of the racks to the ceiling. There are
almost no ceiling tiles in that section as that entire space is the
return back to the CRAC units. It's generally 80 degrees in there. Our
DC strictly enforces gear pulling air in the front and ehausting it out
All cables are above the racks on the cold side. Cold air flows down the
aisles and drops out of the ceiling. As cold air falls that's a win. And
of course hot air rises also a win.
Hot aisle cold aisle is much simpler to maintain when customers are
renting racks rather than cages.
We see a mix of this depending on who built the DC. Raised floors are
very expensive while duct-work is much less so.
- Larry "DrFranken" Bolhuis
www.iDevCloud.com - Personal Development IBM i timeshare service.
www.iInTheCloud.com - Commercial IBM i Cloud Hosting.
On 1/10/2020 11:11 AM, Rob Berendt wrote:
Hot aisle / cold aisle still has the cooling coming from the floor. At least at the GR DC.
As an Amazon Associate we earn from qualifying purchases.
This mailing list archive is Copyright 1997-2022 by midrange.com and David Gibbs as a compilation work. Use of the archive is restricted to research of a business or technical nature. Any other uses are prohibited. Full details are available on our policy page. If you have questions about this, please contact
Operating expenses for this site are earned using the Amazon Associate program and Google Adsense.