currently, the batteries on my system have day counters.
count the number of days up.
count the ADJUSTED number of days up (I see it has a heat check).
count down the number of days to warning.
count down the number of days to error.
Does the system also have checks to see how the batteries ACTUALLY
Wouldn't it be documented somewhere that the
PWRDWNSYS *CNTRLD performs differently
from PWRDWNSYS *IMMED from a disk cache perspective?
On 1/16/2013 1:22 PM, Evan Harris wrote:
My understanding is that the batteries are there to cater forwrote:
precisely this situation.
They (the cache batteries) aren't powered externally; they ensure the
cache guaranteed power and is therefore protected in the case of an
unexpected power loss.
That's why when the cache batteries fail, your performance is degraded
- the system doesn't use the cache as it is no longer guaranteed
On Thu, Jan 17, 2013 at 7:52 AM, Jeff Crosby<jlcrosby@xxxxxxxxxxxxxxxx>
Would the cache batteries have held properly from whenever the UPS
batteries went dead until 1pm?
When unstable utility power was restored at 1pm (9 hours), then some
wouldwould have been coming from the UPS. Since nothing else on the UPS was
powered on, I assume whatever little power was available from the UPS
lighthave been enough to power the control panel/service processor/green
on the front of the system and therefore would be supplying power to the
Does what I just wrote make sense?
This is the Midrange Systems Technical Discussion (MIDRANGE-L) mailing list
To post a message email: MIDRANGE-L@xxxxxxxxxxxx
To subscribe, unsubscribe, or change list options,
or email: MIDRANGE-L-request@xxxxxxxxxxxx
Before posting, please take a moment to review the archives
This mailing list archive is Copyright 1997-2013 by MIDRANGE dot COM and David Gibbs as a compilation work. Use of the archive is restricted to research of a business or technical nature. Any other uses are prohibited. Full details are available here. If you have questions about this, please contact